Three or four copper conductors, stranded and insulated with heat and moisture resistant, chemically crosslinked polyethylene (type RW90 1kV), phase identified and cabled together with bare copper ground conductor(s). Cable core covered with mylar binder tape, inner jacket, aluminum interlocked armour, and outer CPE jacket.
Suitable for use in exposed or concealed wiring in dry or wet locations, in ventilated or ladder type cable trays in dry or wet conditions, on walls or beams, directly buried.
Suitable for use in hazardous locations: Class I - Groups A, B, C and D,
Class II - Groups E, F and G, Class III - All Groups